- LG 113 Home Page
- Distribution Letter
- Equipment Type:
- New! Recent Equipment Type Additions/Revisions
- VPH Methods
- Test Method Index
- Acceptable E85 Leak Detection
- Acceptable Biodiesel Leak Detection
- Leak Detection Equipment Review List
- Acceptable Test Protocols
- Glossary of Terms
- Monitoring System Certification
- Work Group
- Policy Memoranda:
- Maintenance Checklists:
UST Programs - LG 113
Date: December 13, 2013
TLS-4; TLS-4B; TLS-300, 300C, 300i, 300PC; TLS-350, 350-PC, 350R, 350R-PC; 350R; TLS-450 Series; Red Jacket ProMax, ProPlus, and ProPlusPC with Position Sensitive Interstitial Sensor 794380-333
INTERSTITIAL DETECTOR (LIQUID-PHASE)
*The evaluation determined this sensor's responses to the liquids shown above. Biodiesel blends B6-B20 meeting ASTM D7467 and biodiesel B100 meeting ASTM D6751 would also produce an alarm if the sensor threshold is exceeded. Responses to these fuels were not determined, but would be expected to be very similar to the diesel responses.
Sensor will alarm if it is raised from the bottom of the containment. Sensor can easily be removed, cleaned and reinstalled if an alarm is triggered or for periodic testing.
on this list is not to be construed as an endorsement by any regulatory
agency nor is it any guarantee of the performance of the method or equipment.